View and Download Keston C40 installation and servicing instructions online. Fan Powered High Efficiency Modulating Domestic Condensing Gas Boiler. View and Download Keston C40 user instructions online. Central heating condensing gas boilers. C40 Boiler pdf manual download. Also for: C55, C40p, C55p. Keston Boilers Boiler Manuals, Gas Manuals, over Free Gas Boiler Manuals, Keston C36P Combi Keston C40 gc
|Published (Last):||12 February 2004|
|PDF File Size:||16.61 Mb|
|ePub File Size:||1.78 Mb|
|Price:||Free* [*Free Regsitration Required]|
Summary of Contents for Keston C40 Page 1: Extended clearance is required to the front to allow for. The guarantee provided with the Keston C40 and C55 keshon not cover damage caused by system debris or sludge.
Related Documents The C40 and C55 feature an integral frost protection function which will operate the pump, regardless of the external controls, should the boiler temperature fall below 7 C. Don’t have an account?
There must Figure 2. All gas appliances must be installed by competent persons by law in accordance with these.
Fan powered high efficiency modulating commercial condensing gas boiler 49 pages. A gas cock is supplied loose with the boiler. Page 5 Safety footwear and gloves are recommended PPE when lifting this appliance. Boiler Keston Qudos 28s User, Installation Maunal Servicing Instructions Fan powered high efficiency modulating domestic condensing gas system boiler 67 pages.
KESTON C40 INSTALLATION AND SERVICING INSTRUCTIONS Pdf Download.
Fan powered high efficiency modulating domestic condensing gas heat only boiler 65 pages. It is in your interests, and that of safety, to ensure that the appliance is installed correctly and that the. Keston Boilers Ltd declare that manuwl are manal substances harmful to health within the appliance or used during the production of the appliance. The C40 and C55 feature an integral frost protection function which will operate the pump, regardless of the external controls, should the boiler temperature fall below 7 C.
Frost Protection The C40 and C55 have an integral frost protection thermostat. Fan powered high efficiency modulating domestic condensing gas system boiler 72 pages. If fixtures are to positioned close to the boiler the following minimum.
Page 61 If CO levels above these values are experienced, the combustion chamber and flue system should be investigated. Fan powered high efficiency modulating domestic condensing gas combination boiler 68 pages.
If flow cannot be maintained through the system piping to meet the minimums required by kfston boiler, insufficient water flows through the boiler will cause the boiler to “kettle” This log book should be completed by your installer at the end of the installation and commissioning process.
Enter text from picture: Don’t have an account?
Got it, continue to print. By pressing ‘print’ button you will print only current page. Fan powered high efficiency modulating domestic condensing gas boiler 64 pages. Boiler Keston Qudos 28s User, Installation And Servicing Instructions Fan powered high efficiency modulating kfston condensing gas system boiler 67 pages.
If following the above procedure, combustion levels described above at both high and low rate could not be obtained, please turn off the mznual and isolate the gas to the appliance. However, care should also be taken to ensure that any exposed pipework is adequately insulated to prevent freezing.
FREE BOILER MANUALS
To Light The Boiler The C40 and C55 boilers incorporate dual thermostats to allow two different zones to be connected to operate at two different temperatures. This manual also for: There are no user serviceable parts inside the boiler cabinet. Don’t show me this message again.
Fan powered high efficiency modulating commercial condensing gas boiler 49 pages. Fan powered high efficiency modulating domestic condensing gas system boiler 72 pages.
Keston KESTON C40 (Manual and User instructions) Diagram | Heating Spare Parts
It is advisable to fit a locksheild valve on the cylinder return to enable balancing of the flow rate through the cylinder. Page 15 Where ieston stores are to be used the thermal store supplier should be consulted as to the compatibility of the thermal kanual with a Keston C40 and C Generally once per year will be sufficient.
The C40 and C55 models are supplied for natural gas use only. The table below shows the range of status codes which will be